Please upgrade to the new Edge browser, or use Chrome, Firefox or Safari, before continuing. Internet Explorer will not support the best shopping experience on the ADI Digital Branch site after March 12, 2021.
Under normal operating conditions, a low impedance is present between the -IN and -OUT terminals of the base, so that power and signals pass to the next base in line. If a short-circuit or abnormally low impedance occurs, the fall in voltage is sensed and the base isolates the negative supply in the direction of the fault. The isolated section is tested using a current pulse every five seconds. When the short-circuit is removed, the power will automatically be restored. If it is a requirement that no device is lost in the event of a single short-circuit fault, every detector should be fitted to an isolating base. In applications where it is not necessary to use an isolating base for each detector, up to twenty detectors or equivalent surge current may be installed between isolating bases. See PIN sheet PP2090 for full information on loop loading between isolating bases. Consult engineering guides or PIN sheets for quiescent current values of protected devices.
The isolating base is a self-extinguishing polycarbonate moulding with nickel-plated steel terminals for connecting a detector. The associated detector can be locked into the base using the normal locking screw
The isolating base is intended for use with equipment using the Apollo XP95 and Discovery communication protocol.
The Isolating Base senses and detects short-circuit faults on Discovery loops and spurs.
Up to 20 detectors or their equivalent load, may be installed between isolating bases High brightness LED Detects wiring short-circuits Minimises disruption from short circuits
Name : Apollo Smoke Detector Base - For Smoke Detector - Polycarbonate, Nickel Plated Stainless Steel - White, Apollo Fire Detectors, ADI India, Apollo